The Model DCAV uses two recirculatory air curtains, creating an air vestibule between the two air streams where the air is captured and treated to a non-frost, non-fog state.
The Model DCAV automatically adjusts as conditions change to optimize performance and reduce energy consumption.
With the use of HCR sensors and software, Model DCAV can be integrated into a facility's refrigeration control and monitoring system. This allows not only remote monitoring but remote adjusting of the HCR equipment.
- No frost, fog or icing
- Eliminates safety hazards
- No haze within cold room
- Reduced maintenance costs
- No frost on stored products
- Reduced refrigeration loss
- Reduced coil defrosting burden
- Increased warehouse productivity
- Improved refrigeration cycle efficiency
- Sublimates existing frost build-up
Double Conditioned Air Curtain Vestibule, Freezer To Cooler Specifications:Supply where indicated on plans HCR Model DCAV Air Vestibule for doorways between Freezers and Coolers.Air Door to be powder coated cold-rolled steel. Powder coating meets 500 hour salt spray test.NEMA 1 Power/control panel complete. Model DCAV equipment cabinet houses the centrifugal fan and prewired electrical components. Service door(s) are provided, if required, to allow access to all internalcomponents. Motor is controlled by VFD (Variable Frequency Drive). Single point electrical powder connection in most cases.Model DCAV to have four side plenums: two with discharge nozzle, the other two with an intake.Discharge nozzle is easily adjustable to maximize air block. Air volume adjustment mechanisms are easily accessible without removing any covers or secondary openings.Unit can be mounted on either side of wall. Depending on temperature differential insulation cladding may be required.Air Door assembly is structurally self-supporting. All hardware has protective coating against corrosion.Air Door power to be 208, 240, or 480 volt AC, 60 Hertz, 3 phase. Visible signal light to show when motor is not running. Complete door assembly to be ready for connection to power. (Architect to designate responsibility for field wiring.)
Freezer Door SpecificationsSupply where indicated on plans HCR Model DCAV for freezer doorways with temperature differentials greater than 30 degrees Fahrenheit. Provide insulation cladding as may be required for the specific application.Air Doors forming Model DCAV can be mounted either on the warm side, cold side of the wall or split.Electric resistive heat or waste heat reclaim as required.Architectural Data Sheets