The basic NPAC model is made to counteract the one-way flow-through forces caused by negative building pressure or by wind effects.
Supply where indicated on plans HCR Model NPAC Air Door for doorways with low temperature differentials and or for temperatures above freezing.
Air Door to be powder coated cold-rolled steel. Powder coating meets 500 hour salt spray test.
NEMA 1 Power/control panel complete. Model NPAC equipment cabinet houses the centrifugal fan, fan motor, fan drive components, and prewired electrical components. Service door(s) are provide, if required, to allow access to all internal components. Motor is controlled by VFD (Variable Frequency Drive). Single point electrical connection.
Air Door to have two side plenums: one with discharge nozzle, the other with an intake.
Discharge nozzle is easily adjustable to maximize air block. Air volume adjustment mechanisms are easily accessible without removing any covers or secondary openings.
Unit can be mounted on either side of wall. Depending on temperature differential insulation cladding may be required.
Air Door assembly is structurally self supporting. All hardware has protective coating against corrosion.
Air Door power to be 208, 240, or 480 volt AC, 60 Hertz, 3 phase. Visible signal light to show when motor is not running. Complete door assembly to be ready for connection to power. (Architect to designate responsibility for field wiring.)
Options & Accessories
- Metal cladding can be stainless steel or cold-rolled steel powder coated to custom color.
- ‘Clean outs’ can be added where needed.
- Complete NEMA 3, 4, 4x, 4x stainless, or 12 requirements.
- Hot Gas Coil instead of resistive heat.
- Custom standoff panels with trim to interconnect to night doors or existing doors.
- HCR Air Door to be used in conjunction with existing or new door to form a Hybrid solution.
These doors can include all types of insulated roll up doors, double curtain roll up doors, hard insulated automatic doors that slide either horizontally or vertically, or insulated sliding mattress type doors.
1. What factors determine the choice of door solution for an application?
Some of the important factors determining the door type recommendation are the temperature difference across the doorway, opening size, traffic rates, safety concerns, convenience, maintenance, building pressure imbalance, energy savings and etc…
2. Where are HCR air doors made?
HCR air doors are manufactured in Montana, USA.
3. What is the biggest doorway opening size that can be fitted with an HCR air door?
Openings of 14-ft wide and 20-ft high are maximum width and height dimensions that can be fitted with an HCR air door.
4. Which side of the doorway should the HCR air door get installed?
HCR air doors can be installed on either side of the doorway for single air curtains whereas the double and triple air curtain units could also be split mounted. Single air curtains can also be custom designed for doorway jamb mounting.
5. What is an HCR NPAC air curtain?
Negative Pressure Air Curtains are designed for doorways that show pressure imbalance across the opening.
6. What is an “HCR Doorway Survey” form?
An HCR Doorway Survey form is a one page customer completed form summarizing key physical, thermal/environmental, usage and customer desired features of a specific doorway.